My home has these on all the basement windows. As a result, there’s a significant hazard in case of fire. From the pictures, are these just held in place by
I have two black (hot) and two white (neutral) and a ground. One black is hot with braker on and the other is not. What is the likely cause?
I have a switch that controls the room light and all the outlets. I would like to make the outlets always hot. The source of the power is behind the
I would like to replace my ceiling fan with a standard light fixture, however, there is not a wall switch. What are my options if I do not want to
I want to put two 3-way switches in the same box. I’m uncertain what splices I have to make, but I have an educated guess. Rather than explaining it in
As I read the 2014 NEC 210.12 AFCI protection is only required for a "dwelling unit", which would not include a detached workshop. Is that interpretation correct?
I read that subpanels should be mounted to a 3/4" backer board or secured directly to a stud. Can I nail two 2x4s horizontally between two studs and secure the